If you’ve been paying any attention to our blog, you already know how important it is to have a working, well-maintained fire sprinkler system in your building. The most important thing you can do for your fire sprinkler system is have a fire pump big enough to support the whole building. After all, a fire pump that can’t get your sprinkler the water it needs is not much better than having no sprinkler at all!
Fire pumps are sized according to how much pressure they need, measured in gallons per minute (GPM). There are ways to calculate pump GPM: the standpipe method and the sprinkler area calculation method.
A standpipe is a system of piping that firefighters can hook up their hoses to help knock back fires in your building. The standpipe method is governed by NFPA 14, Standard for the Installation of Standpipes and Hose Systems which states that the first standpipe you install in your building requires 500gpm, with each additional standpipe requiring 250gpm up to a maximum of 1000gpm. This is a good method for smaller buildings, but it becomes a problem when a large building requires multiple standpipes.
Sprinkler area calculations are much more involved, but are the best way to size a fire sprinkler system in a large building. To perform sprinkler area calculations, first you need to know the sprinkler hazard classifications of a building and its contents – this will help you determine the design density. Sprinkler hazard classifications are defined as follows:
If a building has different areas with different hazard levels, the highest hazard level present dictates how large the pump will be.
Once pump size calculations have been made, the next thing to do is determine the best type of pump for your building. There are three types of fire pumps:
Commonly called double-suction fire pumps, horizontal split case pumps direct water to both sides of the impeller. These are the most common types of fire pumps, and come rated for 250 – 5000gpm. Horizontal split case pumps were actually the first type of fire pump used for fire protection systems.
There are a few benefits to using inline fire pumps over a different type of fire pump, including a compact, space-saving design and a lower cost of installation.
Vertical turbine pumps are only used in situations where the water supply is below the suction flange, because NFPA standards require positive suction pressure to a fire pump.
As a business owner, it’s probably not important you understand the specifics of how to choose your building’s fire pump. But if you know a little bit more about how your fire protection system works, it can help you make much better decisions about it! If you have a fire pump in Houston and need fire pump inspection or testing, call Kauffman Co. today!
Fire Protection in Houston & Galveston, TX As Texans learned during Hurricane Harvey in 2017, Houston is vulnerable to severe…
Fire Protection Services in Houston & Galveston, TX As warehouses continue to increase in height, incorporate more complicated rack storage…