Buying the right fire extinguisher can make a huge impact on your building’s fire safety. But do you know what to look for when choosing a fire extinguisher?
The different fire classifications are:
ABC fire extinguishers can be safely used on fires involving flammable solids, liquids, and gases as well as those involving electrical equipment. The dry powder is corrosive, so you should be careful and clean it thoroughly after you use it. It should not be your first choice of extinguishers for sensitive electrical equipment (a carbon dioxide extinguisher will work better here).
K Class fire extinguishers are best for cooking oil or fat fires. These extinguisher types smother and cool flammable cooking fat to eliminate the risk of re-igniting. They are also perfect for Class A fires and are not electrically conducive, for added user protection.
CO2 fire extinguishers protect electrical equipment without leaving residue. They can also be used on petrol and oil. Make sure, however, that you never use them on cooking fat fires—the fast discharge has the potential to spread cooking fat around, increasing the area of the fire without putting it out.
All fire extinguishers come with a UL rating that signifies how effective the fire extinguisher is. But the rating may be something like this:
If you can decode that, you might already work in the fire protection industry! For the rest of us, here’s the rating, decoded:
The numbers indicate the relative strength of each extinguisher. For example, 4-A:80-B:C is four times more potent against Class A fires than 1-A:10-B:C, and 4-A:80-B:C is eight times more potent against Class B fires than 1-A:10-B:C.
Fire extinguisher accessories include things like:
If you need new fire extinguishers for your building, it helps to know exactly what you’re getting into. For more information, or to buy fire extinguishers in Houston, call Kauffman Co. today!
Most fire extinguishers don’t come with expiration dates printed on the canister. This is because their lifespan varies widely depending…
NFPA 14 requires all standpipes installed after 1993 to deliver a minimum residual pressure of 100 pounds per square inch…