NFPA 14 requires all standpipes installed after 1993 to deliver a minimum residual pressure of 100 pounds per square inch (psi) at each standpipe outlet, whether installed on the ground floor or the roof. In larger buildings, high-rises, offices with ground-level water tanks, and other similar scenarios, the water pressure may not be sufficient for fire sprinklers and standpipes on upper floors. If this is the case in your building, you need a fire pump to transform a trickle of water into a powerful waterfall to adequately douse a blaze.
Sometimes, adding or upgrading a fire pump results in static and flow pressure higher than the recommended limit of 175 psi. This can damage sprinkler heads and may cause leaking. Even if your system has been in service for decades, increasing the pressure with a new or upgraded fire pump is liable to cause leaks.
One solution to this problem is to install pressure reducing valves, or PRVs.
PRVs control static pressure when no water is flowing and decrease pressure when water is flowing toward sprinkler heads and standpipes downstream of the fire pump. You must know the inlet and outlet pressures to set the “throttle” correctly and control water pressure the way you want at specific points in the system.
The water pressure requirements established in NFPA 14 can be problematic. Let’s say you own and operate a 25-story high-rise building in downtown Houston. It takes nearly 5 psi to push water up a 10-foot riser. This means, to get water from the ground floor to the roof, the fire pump must deliver 125 psi.
This seems doable, but remember, NFPA 14 requires a minimum water pressure of 100 psi at every standpipe outlet. This means, if the ground floor standpipe outlets achieve the minimum 100 psi, the pressure will reach 225 psi by the time the water reaches the roof.
This is where pressure reducing valves come in. You can have several installed on the lower floors of your high-rise building to keep the water pressure below 175 psi while still maintaining at least 100 psi for standpipes and sprinkler heads on the upper floors.
While pressure reducing valves could be right for your situation, they aren’t the only option for changing the water pressure in your sprinkler system. Some of your other options include:
If you think your building requires a fire pump to create adequate water pressure on upper floors, you probably need pressure reducing valves to decrease the pressure on lower floors. Don’t worry—the fire protection experts at Kauffman Co. will work out all the details for you! To learn more, please contact us today.
Fall can be a great time of year in the Houston area. Most of the heat of summer is gone,…
A fire at a commercial property can create devastating losses for the business owners, as well as uncertainty for employees…